[an error occurred while processing this directive]
Posted by BoilingMan on January 22, 2010 at 14:33:26:
In Reply to: Re: Boiler Won't Re-Fire at Set Points posted by Rick Brown on January 13, 2010 at 19:58:04:
Oh, boy! To cancel this guessing game, disconnect your Pressuretrol from boiler and connect it to some source of pressure, Air or Hand pump or whatsoever in parallel vith another pressure gauge. Then slowly rise and drop your pressure and mark ON and OFF READINGS. Do it several times, you will see all points you need. Adjust as you needed. That simple. Good luck.
Post a Followup