[an error occurred while processing this directive]
Posted by dave on January 13, 2010 at 17:11:17:
In Reply to: m4s6000 posted by Dave on January 07, 2010 at 19:10:18:
: looking for ideas on fixing a f30 error code on boiler i just converted it to natural gas i set the pilot pressure to 5.5"wc and moved the electrode further up the pilot with out it causing any havac with the fireeye
ok i pushed the ignition electrode futher up the pilot tube and left the pressre at 5.5"wc the f30 errors have not occured for 5 days now. hoping for the best.
Post a Followup