[an error occurred while processing this directive]
Posted by Mark Whitaker on September 09, 2009 at 14:59:32:
In Reply to: Re: Miura Boiler posted by Vern on May 15, 2006 at 21:24:43:
: : Has anyone had any dealings with MIURA Boiler? I am looking at the EX series 300 hp steam boiler to replace our older Scotch marine units. This is a relatively new product out there. Not much Info available. My Boiler inspector has never seen one. or heard anything as of yet. Any Info good or bad would be appreciated
: The Miuras are extremely fuel efficient. They are also very sensitive to water quality. The local boiler company representing Miura has told me he intends to quit supporting Miuras because they are so much trouble. I have descaled 10 of these units for him, most of which had been in service for less than a year. Upon purchasing the units, the customers were told how important water treatment was, but few listened. After descaling they seem to listen. Some of these customers were not able to descale, they had burned holes in the tubes. The cost of replacing the tubes is enormous. The entire tube, steam drum and blowdown assembly have to be replaced. Apparently Miura won't sell just the tubes. My opinion is stay with a Scotch Marine.
Any Scotch Marine boiler will need water treatment and care as well as a Miura. Miura is just more sensative to it. Especially now, the Miura is the most efficient and trouble free steam boiler avaliable. I would be more than happy to help you out with Miura boilers and any questions you have. www.american-boilers.com
Post a Followup