[an error occurred while processing this directive]
Posted by Paul on March 15, 2009 at 08:17:39:
I have 3 Kewanee boilers and everytime we take emissions readings I notice that our O2 stats and CO2 stats seem to be inverted. Our CO is well within range, under 100ppm, as is our temps, under 400dF, but on low fire our O2 reads around 16 and our CO2 around 6. Shouldn't those readings be switched around?
I am not a licensed operator, but I do supervise operators and I need to ensure what we are doing is correct.
Post a Followup