[an error occurred while processing this directive]
Posted by sunil on November 19, 2008 at 19:17:52:
I just installed a new guage and it is reading 4.5 psi the the boiler shuts off from the CUT-out cut in honeywell switch. I was told 4.5 psi is too hight for a 1 family 2 floor home. I also install a new lower water cut off,automatic water feed....feeding warm water not cold. I replace the pig tail also clean that honeywell part lube and celan the diafram ..the boiler is on and 4.5 shuts off and wait till 2.5 then on again. The CUT in is at .5 psi the the diff is set to 2. From the lable CUT OUT EQUALS TO CUT IN PLUS DIFF..Shoud it not cut out at around 2.5? and not 4.5
Do I need to replace that honeypart also...
Post a Followup