[an error occurred while processing this directive]
Posted by Jeff on August 21, 2008 at 01:07:18:
I have worked on boilers for a long time and have allways been told to pug up to 10%, then retube. I have looked but can not find this in print. I could not even find the words "plugged tube" in the 2007 NBIC. I must settle a score. I would love any guidance.
Post a Followup