[an error occurred while processing this directive]
Posted by Boiler Guy on September 21, 2004 at 06:46:24:
In Reply to: Re: Ohio Special posted by Bob D. on September 21, 2004 at 05:34:59:
: I believe it's the Ohio Administrative Code, Chapter 4101:4-1 thru 4101:4-17. Restricts heat transfer area to roughly 358 sq.ft. for unattended operation.
The other important part of the unique Ohio Special regulations is the number of boilers at the 358 sq ft heating surface restriction does not factor in to the requirement for operators. For example a single 800 HP installation would require operators however four 200 HP Ohio Specials does not even though both scenarios generate a total of 800 HP of steam.
Post a Followup