[an error occurred while processing this directive]
Posted by Tim D on May 20, 2004 at 21:41:02:
In Reply to: Re: Boiler water carryover on New Utica cast iron boiler? posted by Tony Conner on May 19, 2004 at 05:53:22:
: Check the installation instructions for the piping requirements. 8" sounds short. Make sure the 2" connections aren't bushed-down from 2-1/2" or 3". Many problems that are thought to be chemical in origin, are actually mechanical.
The Main supply header is 4" screw pipe from both sides of Utica Boiler. The bottom of the main 4" header to boiler water level is approx 30". Then there are two 4"x2"x4" steam supply tapings (8" tall) on the top of the main header. Our water carry over has minimized this week, but still tend to see some occasionally when at full demand?
Post a Followup