[an error occurred while processing this directive]
Posted by Tim D. on May 17, 2004 at 20:37:39:
In Reply to: Re: Boiler water carryover on New Utica cast iron boiler? posted by Sid on May 17, 2004 at 17:59:11:
: What is the t.d.s. range that you are maintaning in you boiler . What what type of surface bolow are you using
We Maintain conductivity between 1000 & 3000 mohs(u siemen) This past week, conductivity has ranged from 500-1000 mohs.
We can manauly surface skim through a 2" end taping in the 4" steam supply tee by raising water level 2".
Yesterday & Today, there was no carry over? The condensate was clear 25 mohs, ph 8.6.(right where it should be) The boiler water had a conductivity of 850 mohs, ph 10.0 and sulfie 0f 20ppm. Our 3Rd flush (drain & refill) may have made the difference?
Post a Followup