[an error occurred while processing this directive]
Posted by Tom Stanton on March 25, 2004 at 06:02:09:
In Reply to: expansion tank posted by Jack on March 23, 2004 at 12:39:06:
When you say it "now feeds directly into the expansion tank" do you mean it connects directly to the tank or does in connect to the pipe going into the tank? As a NB inspector I use the code. The ASME Setion 4 heating boiler Code under Figure HG 703.2 actually recommends the make up water enter into the pipe that leads into the expansion tank. Under HG 705(b) basically it states the make up water cannot be introduced directly against parts of the boiler exposed to the direct radiant heat from the fire To me it sounds like you are OK.
Post a Followup