[an error occurred while processing this directive]
Posted by Jim Estep on February 01, 2004 at 00:20:34:
In Reply to: Loss of water posted by Bobby Conley on January 28, 2004 at 13:39:18:
: I am running an A frame Nebraska boiler rated at 60,000 pph. It has always been the policy to cool the boiler off if the water level was ever lost and could not be seen in the sight glass. Management now wants water added back to the boiler as as possible when this occurs without waiting for a cool down period. Has anyone ever heard of this????
Post a Followup