[an error occurred while processing this directive]
Posted by Manny. on January 23, 2004 at 08:09:06:
In Reply to: dew point posted by Ilan on January 22, 2004 at 13:13:51:
As long as you keep your feedwater going into the economizer over 200 degrees,you will not condense.Do not put water into the unit under 200 degrees or you will condense and void out your warranty.Also only put water that has gone thru your D.A tank and has at least 4 to 6 ppm of soduim bi sulfite in it,or you will pit it up so fast,and have leaking tubes in no time.
Post a Followup