[an error occurred while processing this directive]
Posted by Tony Conner on April 05, 2005 at 15:49:27:
In Reply to: Re: Glycol system air bleeders posted by GeneratorGrrl on April 05, 2005 at 14:15:23:
The thing to remember is that you want the air separator located where the liquid is closest to the boiling point. That will be the highest temperature (right after the boiler) and the lowest pressure which is right after the expansion tank, but before the pump suction. Bell & Gossett have some excellent info on these systems.
Post a Followup