[an error occurred while processing this directive]
Posted by Orville on March 10, 2005 at 23:22:04:
One other detail I failed to mention in my first message: we blow soot once per shift, and the steam we use comes directly out of the steam drum as opposed to coming off the main header line. What pressure is best for blowing boiler and economizer tubes? We carry 230 psi on our boilers. Also, I think we are getting a lot of condensate out of the steam drum. Would it be wise to relocate the steam supply to the main header line? Thank you.........
Post a Followup