[an error occurred while processing this directive]
Posted by Lewis on October 27, 2004 at 17:36:09:
In Reply to: Boiler blowdown rate posted by Ramendran on October 09, 2004 at 00:16:42:
The way we calculate surface blowdown in the U.S. Navy is with this formula:
Conductivity before surface blow subtracted by Conductivty after surface blowdown divided by Conductivty before, multiplied by 100.
This is refering to the boiler water conductivity.
Post a Followup