[an error occurred while processing this directive]
Posted by Daniel Lapierre on May 08, 2005 at 13:41:57:
In Reply to: Who Can service A Trianco-Heatmaker in New Haven, Ct? posted by David Duda on November 28, 2001 at 08:51:58:
For mamintenance manual on Trianco Heatmaker Mark II check the home site. http://heatmaker.com/
Had a problem with domestic hot water which turned out to be caused by a stuck open and corroded check valve. Hard water was the true source of the problem. Cleaned the valve and the low limit switch now works as designed. Also put Hercules boiler compound in the boiler to correct the water problem. This will prevent furthur corrosion of the boiler and it's components. Check the manual; it is really good and has an excellent troubleshooting flow chart. Yoy can download it from the internet.
Post a Followup