[an error occurred while processing this directive]
Posted by gbemi adiio on September 24, 2005 at 07:44:04:
In Reply to: Re: calculate efficiency posted by gburns on May 02, 2001 at 12:55:50:
: Using the heat loss method you can calculate the boiler efficiency but you will not need steam flow, however, you will need more information than what you listed.
: You will need:
: the steam pressure and temperature,
: the feedwater temperature and pressure,
: combustion air temperature,
: O2 leaving the boiler,
: Flue gas leaving the boiler,
: Fuel analysis,
: This test method is available as part of PTC 4.1 through ASME.
: : How can you calculate approx. efficiency when you only know steam flow water flow and exhaust gas temp?
Post a Followup