[an error occurred while processing this directive]
Posted by Bob Dooley on August 02, 2002 at 10:58:57:
In Reply to: Sootblowing steam desuperheater posted by Greg B on August 02, 2002 at 06:50:43:
Just a suggestion - see if you have a take-off of adequate size from the steam drum before the superheater section, or tee off of the cross-over piping, so you don't have the superheat issue at all. Just be sure that there is still enough steam flow through the superheater tubes to prevent overheating. You might have to have the boiler manufacturer "bless" this approach.
Post a Followup