[an error occurred while processing this directive]
Posted by J . Baughman on July 29, 2002 at 05:19:51:
In Reply to: stack economizers posted by m white on July 23, 2002 at 09:28:28:
: does anyone have an opinion on stack economizers?
: this would most likely be for a 100bhp firetube boiler, burning #2, and total operating hours for the year are estimated to be 1300-1400 hours. is it worth it or am i just setting myself up for a major maintainence issue?
On #2 you`ll be cleaning coils regularly of soot.
Not sure it`s worth it for that few hours of run time,the efficiency savings would be minimal.
Post a Followup