[an error occurred while processing this directive]
Posted by Joe Lambert on July 15, 2002 at 05:44:42:
In Reply to: Re: Online condensate monitoring posted by Vern on July 12, 2002 at 21:11:06:
Unfortunately, Glucose will not be picked up by a TDS monitor because it is an organic. I ran into this problem in a sugar refinery, the boiler turning into a huge cotton candy maker. The best we could do is hook up an on-line turbidity monitor because the burnt sugar was black, although this did not prevent the initial contamination, it did help. A company called GESTRA makes both turbidity and conductivity monitors specifically for condensate.
Post a Followup