[an error occurred while processing this directive]
Posted by pete on May 24, 2002 at 10:53:51:
In Reply to: Boiler feeding line Water hammering posted by BoilingMan on May 22, 2002 at 11:37:51:
Your water hammer may not be temperature related but from a sudden reverse in water velocity when you stop a pump, causing your swing check to slam closed causing a pressure wave. You may want to try closing the gate discharge valve first before shutting down or starting a pump to see if this eliminates the hammer.
Post a Followup