[an error occurred while processing this directive]
Posted by gburns on April 10, 2002 at 19:22:22:
In Reply to: Re: Vented Flash Tank Requirements posted by Todd Spacek on April 09, 2002 at 19:38:59:
In my previous posting I used as an example continous blowdown tank. Because this is clean condensate I did not want to sound as though I was recommending putting this stream to a boiler continuous blowdown tank as that eventually goes to sewer. However, running it to a similar type tank which flashes to a medium or low pressure header would be the best alternative. It all depends on steam incremental costs as well as boiler make up incremental costs and whether putting in a tank will give you a positive return on your $.
Post a Followup