[an error occurred while processing this directive]
Posted by brian on March 20, 2002 at 19:36:01:
In Reply to: Re: mud drum blow down posted by Tom Stanton on March 20, 2002 at 09:36:54:
In Massachusetts the outlet of the blowdown tank cannot exceed 150 degrees F, so most of the tanks have a solenoid operated tempering water valve that admits city water to cool down the discharge. If you tank is used strictly for blowdown, and you are not recovering any flash vapor, make sure it is safely vented to the atmosphere.
Tom, could you go more into detail about the Mass law for the blow down.
Post a Followup