[an error occurred while processing this directive]
Posted by BoilingMan on February 21, 2002 at 06:50:21:
I have 2 100 Lb steam boilers in operation.
At what level should be set secondary water level Cut Off device regardind the main McDonnel?
1/2 " below is OK? Or there is sertan requirement?
I could not find it.THANKS!
Post a Followup