[an error occurred while processing this directive]
Posted by mike on February 10, 2002 at 08:12:25:
In Reply to: Re: FLOOD posted by Harold Kestenholz - hydronic.net on January 10, 2002 at 19:45:29:
: Well, a cast-iron radiator in the home sits there in the room cooling off steam that is sent to it; the condensate returns down the pipe to the boiler.
: A boiler sits next to another on a common header. The steam that is sent to it from the other boiler hits the large steaming surface; the same size surface as in the steam drum of the unit that is firing. The steam turns to condensate but IT HAS NO OTHER PLACE TO GO.
i think i am going to install a stean trap to the equalizing pipe on the rear of the steam drum to dump cond. to cond. tank should cure flooding
Post a Followup