[an error occurred while processing this directive]
Posted by JIM on January 19, 2002 at 13:11:35:
In Reply to: Inverted bucket trap posted by Tom M. on January 18, 2002 at 09:50:13:
: After overhauling an inverted bucket trap, what must be done before returning it to service
An inverted bucket trap some times requires priming. This is accomplishe by shutting the outlet valve long enough to build up condensate and then slowly opening it.
Post a Followup