Posted by Tony Conner on August 26, 2001 at 07:28:35:
In Reply to: condensate return from the main steam header posted by ED MATTHEWS on August 25, 2001 at 19:05:51:
With the trap discharge going to the suction side of the feedpump, I think that if (when?) the trap blows through, you'll run the risk of cavitating the pump. Take the discharge to a condensate tank, or directly back to the DA.
Post a Followup