Posted by dado on August 04, 2001 at 04:51:48:
in a 350 psi water tube boiler of capacity 5 tons steam generation recieving about 50 percent condensate & using 50 percent zeolite treated soft water.when the boiler water side is inspected after one year how much scale can be expected? or boler should show not even a trace of scale? can such an ideal situation exist with the above considered conditions or it is practically impossible.
Post a Followup