Posted by Tarzan on June 27, 2001 at 14:40:39:
In Reply to: Regarding fake message to TARZAN !!! posted by BoilingMan on June 25, 2001 at 07:14:01:
: Hey Guys I thing, we do some serious business up here.
: Pleas do not turn this site to kids Chat room at AOL.
: I donít know Who is that smack, cheating here,
: but it is Unacceptable!!
: THANKS = BoilingMan =
Some guy is just foolin around. Don't take it so personal....by the way, what's a "smack"?...
What did you decide to do with your broken LWCO device?
While I was looking for lightning damage, I found a corroded micro switch on a main gas valve proof of closure that indicated high resistance. Replacing it took care of the spurious shut downs and fail-to-fire problems we have had for some time.
Post a Followup