Posted by Tarzan on June 18, 2001 at 09:46:15:
In Reply to: Lighting Strike-HELP ! posted by Tarzan on June 15, 2001 at 09:35:31:
: # 2 Boiler hit by lighting last night....down hard....goes thru ignition sequence up till the fuel and blower rack starts to move to post purge position, but before they get there it trips with "Flame failure" indication.....doesn't get a chance to make the switches that allow it to advance to "spark and pilot" before it trips out.....AARRRGGGHHH!
: Ideas anybody?
We got it!....purge cycle timer was fried...jumpered it out and boiler fires like a cannon....now I gotta find an antique honeywell timer....AAARRRGGGHHH!....Might just wire in the alarm clock I had rigged to blow my ex's car...the little huzzy gets a reprieve.
Post a Followup