Posted by jim z on May 24, 2001 at 18:15:22:
In Reply to: Re: Minimum Gas Pressure at the Burner posted by Raymond on May 23, 2001 at 08:31:43:
: : I have a 200 HP Cleaver Brooks boiler,Natural Gas.
: : I need to figure out minimum gas pressure at the burner.
: : Currently I have Max 5.2 in.wc and Min. 0.2 in.wc.
: : at High and Low fire respectively. And boiler still
: : cycling on low fire, when load demand is minimum.
: : Is there any way to downsize boiler HP ?
: : Thanks BoilingMan.
: Contact your burner manufacturer. Diminish the size of your burner orifices.
Post a Followup