Posted by Raymond on May 23, 2001 at 08:31:43:
In Reply to: Minimum Gas Pressure at the Burner posted by BoilingMan on May 23, 2001 at 08:14:07:
: I have a 200 HP Cleaver Brooks boiler,Natural Gas.
: I need to figure out minimum gas pressure at the burner.
: Currently I have Max 5.2 in.wc and Min. 0.2 in.wc.
: at High and Low fire respectively. And boiler still
: cycling on low fire, when load demand is minimum.
: Is there any way to downsize boiler HP ?
: Thanks BoilingMan.
Contact your burner manufacturer. Diminish the size of your burner orifices.
Post a Followup