Posted by mike on February 20, 2000 at 18:34:34:
In Reply to: Re: boiler posted by Rick Bullard on February 11, 2000 at 09:46:24:
: : Today we had a boiler that had the o2 go from 4.2 to 9.2,also the sides of the boiler started pulsating. it was pulling about 40000. We have Preferred Instruments Controls.Any Help ?
: The increase in O2 indicates an increase in excess air. I'd check the FD and/or ID fan controllers or the oxygen trim controller if you have O2 trim. The furnace was pulsating from an excessive amount of fuel-gas being carried through it.
also check your safeties on feed water heater to make sure they are not drawing in air! thsi is were O2 might be coming in!
Post a Followup